View and Download Keston C40 installation and servicing instructions online. Fan Powered High Efficiency Modulating Domestic Condensing Gas Boiler. View and Download Keston C40 user instructions online. Central heating condensing gas boilers. C40 Boiler pdf manual download. Also for: C55, C40p, C55p. Keston Boilers Boiler Manuals, Gas Manuals, over Free Gas Boiler Manuals, Keston C36P Combi Keston C40 gc
|Published (Last):||5 January 2011|
|PDF File Size:||15.15 Mb|
|ePub File Size:||20.44 Mb|
|Price:||Free* [*Free Regsitration Required]|
KESTON C40 INSTALLATION AND SERVICING INSTRUCTIONS Pdf Download.
This log book should be completed by your installer at the end of the installation and commissioning process. If CO levels above these values are experienced, the combustion chamber and flue system should be investigated. If following the above procedure, combustion levels described above at both high and low rate could not be obtained, please turn off the appliance and isolate the gas to the appliance.
The details of the Checklist will be required in the event of any warranty work being required. Installation of the boiler is straightforward but consideration must be given to access to allow flue and air pipes to be pushed through walls and ceilings.
Fan powered high efficiency modulating domestic condensing gas combination boiler 68 pages. Extended clearance is required to the front to allow for.
Contact Keston Boilers Ltd for information 2. Further information regarding these regulations can be obtained from your. Check the electrode assembly mounted on the heat exchanger.
If the point is damaged d40 burnt replace it. Fan powered high efficiency modulating domestic condensing gas boiler 64 pages.
Fan powered high efficiency modulating domestic condensing gas combination boiler 80 pages. C55C40pC55p. Also See for C40 Installation and servicing instructions – 61 pages. Don’t show me this message again.
They are designed for use with fully pumped systems only. Generally the central heating zone is connected to zone 1 and the hot water cylinder to zone 2. Don’t have an account? These krston should be carefully read to ensure safe and economical. Fan powered high efficiency modulating domestic condensing gas heat only boiler 65 pages.
FREE BOILER MANUALS
Summary ketson Contents for Keston C40 Page 1: If fixtures are to positioned close to the boiler the following minimum. The C40 and C55 boilers can be fitted in compartments with very small clearances required around the appliance refer to Section 1.
Modulating condensing combination gas fired boiler 54 pages. Since the units use standard 50 mm muPVC pipe for the flue and air intake systems the boiler is packed in a single box without additional flue kit. To ensure continual safe and efficient operation of the boiler it is.
Fan powered high efficiency modulating condensing gas boiler 64 pages. Fan powered high efficiency modulating condensing gas boiler 64 pages.
To Light The Boiler The C40 and C55 boilers incorporate dual thermostats to allow two different zones to be connected to operate at two different temperatures.
Keston KESTON C40 (Manual and User instructions) Diagram | Heating Spare Parts
Don’t show me this message again. Fan powered high efficiency modulating domestic condensing gas combination boiler 80 pages. Recommended Handling Procedure 0. Page 15 Where thermal stores are to be used the thermal store supplier should be consulted as to the compatibility of the thermal store with a Keston C40 and C Installation of air bleed valves at the high spot s in the system will allow for air elimination when filling the system and will allow re-venting in a day or so after all air has been driven out of solution.
Page 53 If following the above procedure, combustion levels described above at both high and low rate could not be obtained, please turn off the appliance and isolate the gas to the appliance. For LP gas, carbon dioxide CO mnaual will be between 9.