ULC is pleased to announce the publication of the Fifth Edition of CAN/ULC- S, Standard for. Inspection and Testing of Fire Alarm Systems. This National. Fire Alarm Inspection, Maintenance, and Service by Anubis Systems Technologies. SCOPE. This Standard provides requirements for the inspection and testing of fire alarm systems and specifies the devices and functions to be inspected.
|Published (Last):||8 November 2008|
|PDF File Size:||9.57 Mb|
|ePub File Size:||7.48 Mb|
|Price:||Free* [*Free Regsitration Required]|
Special Inspection Postal Code: Manual transfer from alert signal to alarm signal. Common audible trouble signal operates.
Ancillary devices, which are powered from the control unit or transponder, are recorded. Circuit Disconnect Means Location: Output circuits for selective voice paging, including visual indication, F operates. The communicator has been placed back into service. There is a possibility that you may inadvertently set off the fire alarm system.
Standards Council of Canada
Individual alarm and supervisory input zone designation labels are properly identified. Cap gaskets in place and in good condition?
Gauges tested and calibrated or replaced? Refer to Appendix F1 ; P iii Silent accelerated test.
This form is intended to provide the owner or fire inspector with an overview of what fire protection systems exist in the building and which systems were inspected and tested by a qualified technician. Smoke control installed in accordance with Measure: Please contact us for more information. G Confirm that the supervisory transmission to the fire signal receiving centre is received. The printed maintenance and testing guide must be followed.
CAN/ULC-S536-04 Fire Alarm Annual Inspection Test Form
Description of elevator homing functions caj by the fire alarm system. Lined Unlined Supply water pressure: Indicate type of test performed on a fully charged battery select one: Nozzle clips in place and nozzles contained?
Switches for ancillary functions operate as per design and specification. Supporting documentation attesting to this is on site and has been reviewed. Please review additional Article 9 testing requirements on the Passive Systems page.
CAN/ULC-S Fire Alarm Annual Inspection Test Form
The fire signal receiving centre transmitter is located remotely from the fire alarm control B unit. All control valves operated thru full range and returned to jlc
Recommended Additional Testing not mandated 40 the Standard: Photoelectric type smoke detectors utilize an infrared light source called the emitter and a receiver, both of which are located inside the sensing chamber. Tested for Operation results are recorded in the Device Test Record. Instructions for silencing the trouble signal and action to be taken when the trouble signal sounds.
CAN/ULC-S | Standards Council of Canada – Conseil canadien des normes
There are a total of: Glass break device in place? Record the date, revision and version of firmware: Have modifications or uc been done since the last inspection?
Good Worn Inspect electrically supervised valves? Jockey pump operational and in good condition?